Ground Source Heat Pumps Explained
The heating industry is going through one of the most important revolutions at the moment, with the introduction of new low-carbon-emission heating technologies.
Heat pumps are effectively reverse air conditioning systems. They use low temperature heat source and convert it into a much higher temperature that can be used for water heating and general domestic heating. Using initial heat from the ground, together with the high efficiency of the heat pump will save a large amount of carbon dioxide emissions that would other wise be expelled into the atmosphere under traditional heating systems.
Heat pumps, especially ground source ones, are getting increasingly popular world wide with extra focus in the American and European markets. According to estimates, there are approximately 550,000 units installed world wide (of which 80% are domestic), and there are about 66,000 annual installations on going.
Heat pump technology is well used around the world. However, the UK market is lagging behind, with low level of awareness. This is likely to change, as a quality system offers excellent performance and significantly reduce carbon dioxide emissions and provide efficienct space heating.
Types of Heat Pump Systems
A typical ground source heat pump system has a ground heat exchanged, a water-to-water or water-to-air heat pump, and a heat distribution system, see chart below for a typical system’s layout.
Ground source heat pumps are used for space and domestic water heating, as well as for cooling of buildings of various types and sizes. It is important to note that using ground source heat pumps for cooling will result in increased energy consumption.
Ground source heat pumps are especially suitable for new buildings, as the low temperature provision is perfectly suited to the demand of under-floor heating systems. They are also appropriate for installation in existing homes, especially when reducing heat demand. They can be financially attractive in areas where there is no coverage the mains gas grid or for developments that are planned to simplify the infrastructure.
It important to get as high a temperature as possible from the ground, as well as keep the output heating temperature low to maximise the efficiency of the ground source heat pump system. Ground source heat pumps have typically higher efficiency than air source heat pumps, as the ground temperature is warmer than air temperature in the winter and cooler in the summer. A relatively stable ground temperature allows the heap pump to operate close to it s optimal design point, while changing air temperatures are much more volatile, both daily and on a seasonal level.
A ground source heat pump which supplies low temperature heating system (e.g. under-floor heating), will have seasonal efficiency of 300%-400% for indirect system and even higher (350%-500%) for direct systems. As reference, the seasonal efficiency of an air source heat pump is about 250%. Seasonal efficiency is the ratio of energy delivered from the heat pump to the energy supplied to it, averaged over a year (this includes energy required for circulation of the liquid inside the ground loops).
The high efficiency of the ground source heat pumps is minimising the electricity demand, and the respective CO2 emissions that goes with it. The next example demonstrates the low carbon emission and high efficiency of the ground source heat pumps.
With an average CO2 emissions factor for electricity of o.414 Kg/kWh, a ground source heat pump with a seasonal efficiency of 350% would yield emissions of 0.12Kg of CO2 for every kWh of useful heat delivered. A high efficiency condensing boiler, with efficiency rating of 85% and CO2 emissions factor of 0.194 for gas, would result in 0.23Kg of CO2 for every kWh of useful heat delivered. This shows that the CO2 emissions from a high efficiency boiler is almost double that of a ground source heat pump for the same unit of heat delivered. However, it is fair to note that during peak demand, some electricity provided to the heat pump may come from less efficient power stations with a CO2 factor that is as high as 0.8Kg CO2/kwH.
Ground source heat pumps have other advantages:
When considering ground source heat pumps, it is essential to get a very clear analysis of the building’s heat loss, related energy consumption and the requirement for domestic hot water. A detailed calculation of these parameters will help determine an accurate size for the heat pump system, which is more crucial than traditional heating systems (such as condensing boiler), because the initial capital costs of a ground source heat pump system is much higher.
The design should avoid over sizing the system, as it will increase the initial costs, as well as make the system operate under part load, thus making it less efficient and more expensive. Equally, under sizing should also be avoided, as the system will not be able to cope with the heating demand, requiring top up heating with will reduce overall efficiency of the system.
A ground source heat pump can be designed to deliver all heating requirement. However, it might be more economic to design a dual system, where the heat pump covers the base heating load with an additional system to cover the peak periods.
Reducing the output temperature from the heat pump will increase its performance. Heat pumps normally provide output temperature limited to 50-55c for most application. This temperature is not high enough for heating systems with radiators heat distribution set up.
The depth of the ground loop is an important factor, especially when taking into account issues of the type of soil, rock and ground temperature. The temperature difference between the ground and the antifreeze fluid inside the loop is what is driving the heat transfer. The ground will show seasonal temperature swings at depths of up to 2m. If the depth is increased, the seasonal variations diminish and begin to lag the temperature on the surface. At a depth of about 1.5m the time lag is around one month. Below 10m the ground temperature remains virtually constant at 10-14c (depending on local geology and soil conditions).
The Environment Agency will not normally withhold permission/authorisation for closed loop ground source heat pumps. The agency, nevertheless, may provide comment on proposed systems where there is a risk of pollution to groundwater. Where these is a realistic risk of pollution to groundwater the Environment Agency may serve statutory notices to protect the groundwater.
The Heat Pump
Ground source heat pumps operate through a wide range of incoming water temperatures. Typically, water coming in at a temperature within a range of -50c to +120c with the heat pump delivering output temperature of 50c – 55c.
Heat Distribution System
The lower the required output temperature from the heat pump the more efficient it gets. Alternatively this can be compensated by higher input temperature (e.g. warmer ground), which would also improve the efficiency of the pump and the subsequent economic benefit. If, for example, the required temperature from the pump is reduced from 600c to 400c, the coefficient of performance can increase by more than 40%.
Table showing supply temperature requirement for several heating systems:
This page has been written with contributions from plumbers from Buckinghamshire and experienced heating engineers from Putney. Several of the company's heating engineers from Surrey have worked on similar issues as well as some of our plumbing and heating engineers from Enfield and our Hendon experienced plumbers.
I was very happy with the plumber, he was professional
Keep up the good work. We have used your gas engineers...